The Smoke and Heat Detector works around the clock to ensure the customer is protected from heat damage. Paired with our monitoring, it is the key to peace of mind.
Manufacturer/Model Number: Interlogix RE114
Dimensions: 4.7 x 1.8 inches (12.0 x 4.6 centimeters)
Battery: Two Panasonic CR123A
Battery Life: 5 Years
Weight: 7.36 ounces
Compatibility: Simon XT Panel, IQ Panel, Frontpoint Hub
Operating Temperature Range: 40 °F to 100 °F
Smoke Sensitivity: 1.95% to 4% OBS/Foot
Heat Detection Fixed: 135 ± 5°F (57 ± 2°C)
Smoke Sensor: Photoelectric
The siren is Approx. 85 decibels.
This sensor cannot be used for businesses or any other commercial environment. They do not meet state or national fire codes for new home construction, or for existing home renovations. Systems required by code are not required to be monitored, which makes the use of our sensors only as supplemental devices a logical method of increasing safety and peace of mind.
This device does not adhere to the MD law taking effect in 2018 about battery-operated SDs. We received a letter from the Fire Marshal of MD stating that our equipment is exempt from this law. It refers to the type of standalone smoke alarms that are purchased at hardware stores typically. Because our sensors are part of a monitored and comprehensive alarm system, they are permissible in the state of MD.
A common hallway shared by multiple bedrooms
In a central room in the home.
If the appliance is in a room not normally used, the smoke alarm can be placed just outside the room so that the alarm will be heard more easily.
Where Not to Place
Kitchen, garage, or room containing a furnace
Near heating/cooling vents, flues, chimneys, or any other air ventilation openings
Near a shower or another potentially humid area
Avoid placing in an area with a large quantity of metal or electrical wiring or near wiring/ light fittings in general
Near ceiling fans, doors, windows, or other areas exposed to weather
Avoid dead air spaces, such as the top of a vaulted ceiling, as this may not detect smoke in time to provide early warning
Next to surfaces that are normally warmer or colder than the rest of the room
Near a furnace, space heater or hot water heater
Where dirt or dust could block the sensor
Avoid very high or awkward areas
Make sure the surface is clean and dry. If you’re placing the sensor on a ceiling, mount it 4 inches away from the wall. If you're placing it on the wall, mount it 4 to 12 inches below the ceiling.
Once the wax backing is removed from the adhesive, press the sensor firmly against the wall or ceiling for 30 seconds.